Rated voltage 0.6/1kv PVC insulated and sheathed (flame retardant) power cables comply with GB/T 12706.1-2008, which is equivalent to IEC 60502-2004, the flame retarding property complied with GB/T18380-2008.Operating characteristics
Allowable long-term working temperature for cable conductor should be no higher than 70℃, and Max. temperature can’t exceed 160℃ in short circuit (Max. duration not exceed 5S). Ambient temperature should be not minus in cable laying. The cable can be installed without limitation of drop falls and easy for maintenance & repair.
Min. bending radius of non-armored cables should be no less than 10 times of cable outer diameter, and 12 times of armored cables, 15 times for five-core cables.Range of application
This product applies in power transmission and distribution in lines with rated voltage 0.6/1kV (flame retardant cable are applied in high buildings, subways, power stations, large industrial and mining enterprises where there are large installation density and strict requirement on fire resistance).